Please use terminal [FMA] or terminal [FMP] and output.
About terminal [FMA]
The terminal [FMA] outputs monitor signals of analog DC voltage DC 0 to + 10 V or analog DC current DC + 4 to +20 mA. The content of the signal, F31 (Terminal [FMA] (function selection))).
DC 0 to + 10 V output - Connectable Impedance: minimum 5 kO
Up to two instruments with analog voltmeter (DC 0 to + 10 V, input impedance 10 kO) can be connected.
DC + 4 to + 20 mA output - Connectable Impedance: Maximum 500 O
The gain adjustment range is 0 to 300% for both current and voltage.
About terminal [FMP]
The terminal [FMP] outputs a pulse signal.
The content of the signal, F35 (Terminal [FMP] (function selection))).
Connectable Impedance: Minimum 5 kO
Up to two analog voltmeters (DC 0 to + 10 V, input impedance 10 kO) can be connected.
Pulse duty: About 50%
Pulse rate: 25 to 6000 p / s (at full scale)
About contents of signal
The signal contents of both of the above terminal functions are as follows.
0 : Output frequency 1 (before slip compensation)
1 : Output frequency 2 (after slip compensation)
2 : Output current
3 : Output voltage
4 : Output torque
5 : Load factor
6 : Power consumption
7 : PID feedback value
8 : PG feedback value
9 : DC intermediate circuit voltage
10 : Universal AO
13 : Motor output
14 : Analog output test (+)
15 : PID command (SV)
16 : PID output (MV)
17 : Sync angle deviation
One point advice
To switch between the voltage output and the current output of the terminal [FMA], SW4 on the printed circuit board F29 (Terminal [FMA] (operation selection)) must be switched. Please change according to the output method to be used according to the table / figure below.